Tray Cable - Power & Control Composite Cable
600 Volt UL Type TC-ER*
General purpose cable for use in power, control and lighting circuits in a broad range of commercial and industrial applications. Approved for installation indoors or outdoors, aerially, in conduits, ducts, cable trays or direct burial in circuits not exceeding 600 volts. May be used in NEC Class I and II, Division 2 hazardous locations. UL approved for use in continuous operation at 75°C in wet locations, 90°C in dry locations, 130°C for emergency overload conditions, and 250°C for short circuit conditions.
7-strand soft bare annealed copper per ASTM B-3, Class B stranding per ASTM B-8.
Flame-retardant PVC per UL Standard 83 for Type THHN or THWN wire.
Clear nylon per UL Standard 83 for Type THHN or THWN wire.
Soft bare annealed copper per ASTM B-3, Class B stranding per ASTM B-8 sized in accordance with UL Standard 1277.
Sunlight-resistant PVC per UL Standard 1277.
All data subject to change without notice