Designed and constructed to be a flexible alternative to Type MC cable where crush and impact protection in arctic conditions is required.
Ampacities are based on Table 310.16 of the National Electrical Code (NEC) for conductors rate 90°C, in a multi-conductor cable, at an ambient temperature of 30°C. The 75°C column is provided for additional information. The ampacities shown apply to open runs of cable, installation in any approved raceway. Derating for more than three current carrying conductors within the cable is in accordance with NEC Table 310.15 (B) (2) (a). Ampacities shown also apply to cables installed in cable tray in accordance with NEC Section 392.11.
Gexol cross-linked flame retardant polyolefin, meets requirements for Type P of IEEE 1580 and Type X110 of UL 1309/CSA 245. 600V/IEC 1000V.
HWC also specializes in hard-to-find specialty items. The HWC team is always concerned with filling customers' orders as properly and efficiently as possible. And if it's not in stock, HWC will get it- no problem! Get A Quote
With over 30,000 products sold annually, Houston Wire & Cable provides its customers with knowledgeable market and product application experts, standard same-day shipments, 99.99% order accuracy and on-time delivery, and 24/7/365 service.Choose...